- •New point-of-use (POU) faucet and shower filters effectively removed Legionella for 12 weeks.
- •A literature search found 20 published peer-reviewed articles about POU filters.
- •Features of 53 POU filters are reported to allow facilities to compare and select from among the various filters available.
- •Infection preventionists and facilities staff should collaborate on water safety.
Purchase one-time access:Academic & Personal: 24 hour online accessCorporate R&D Professionals: 24 hour online access
One-time access price info
- For academic or personal research use, select 'Academic and Personal'
- For corporate R&D use, select 'Corporate R&D Professionals'
Subscribe:Subscribe to American Journal of Infection Control
- Waterborne nosocomial infections.Curr Infect Dis Rep. 2000; 2: 490-496
- Vital signs: health care–associated Legionnaires’ disease surveillance data from 20 states and a large metropolitan area—United States, 2015.MMWR Morb Mortal Wkly Rep. 2017; 66: 584-589
- ANSI/ASHRAE Standard 188-2018.Legionellosis: risk management for building water systems. American Society of Heating, Refrigerating, and Air-Conditioning Engineers, Atlanta (GA)2018
Centers for Medicare & Medicaid Services. Requirement to reduce Legionella risk in healthcare facility water systems to prevent cases and outbreaks of Legionnaires’ disease (LD). Available from: https://www.cms.gov/Medicare/Provider-Enrollment-and-Certification/SurveyCertificationGenInfo/Downloads/QSO17-30-HospitalCAH-NH-REVISED-.pdf. Accessed September 25, 2019.
- Developing a water management program to reduce Legionella growth and spread in buildings: A practical guide to implementing industry standards.Centers for Disease Control and Prevention, Atlanta (GA)2017
Environmental Protection Agency. Contaminant candidate list 4-CCL 4. Available from: https://www.epa.gov/ccl/contaminant-candidate-list-4-ccl-4-0. Accessed September 25, 2019.
- What's in your water? Waterborne bugs can cause fatal infections.Hosp Infect Control Prevent. 2015; 42: 61-65
- Safe water in healthcare premises.J Hosp Infect. 2016; 94: 1
- Drinking water microbiology—from measurement to management.Curr Opin Biotechnol. 2015; 33: 87-94
- Role of environmental surveillance in determining the risk of hospital-acquired legionellosis: a national surveillance study with clinical correlations.Infect Control Hosp Epidemiol. 2007; 28: 818-824
- Point-of-use water filtration reduces healthcare-associated infections in bone marrow transplant recipients.Transpl Infect Dis. 2010; 12: 238-241
- Maintaining Legionella control in building water systems.J Am Water Works Assoc. 2014; 106: 24-32
- Free chlorine and monochloramine inactivation kinetics of Aspergillus and Penicillium in drinking water.Water Res. 2017; 120: 265-271
- Experiences of the first 16 hospitals using copper-silver ionization for Legionella control: implications for the evaluation of other disinfection modalities.Infect Control Hosp Epidemiol. 2003; 24: 563-568
- Preventive efficacy and cost-effectiveness of point-of-use water filtration in a subacute care unit.Am J Infect Control. 2010; 38: 69-71
- Efficacy of new point-of-use water filter for preventing exposure to Legionella and waterborne bacteria.Am J Infect Control. 2005; 33: S20-S25
- Field evaluation of a new point-of-use faucet filter for preventing exposure to Legionella and other waterborne pathogens in health care facilities.Am J Infect Control. 2014; 42: 1193-1196
- Removal of waterborne pathogens from liver transplant unit water taps in prevention of healthcare-associated infections: a proposal for a cost-effective, proactive infection control strategy.Clin Microbiol Infect. 2014; 20: 310-314
- Dye-containing buffered charcoal yeast extract medium for the differentiation of members of the family Legionellaceae.J Clin Microbiol. 1981; 13: 380-382
- Water quality - detection and enumeration of Legionella.International Organization for Standardization, Geneva, Switzerland1998: 1-16
- Water quality - detection and enumeration of Legionella. Part 2: Direct membrane filtration method for waters with low bacterial counts.International Organization for Standardization, Geneva, Switzerland2004
- Standard test method for isolation and enumeration of Pseudomonas aeruginosa from water.American Society for Testing and Materials, West Conshohocken (PA)2013
- Standard methods for the examination of water and wastewater.21st ed. American Public Health Association, American Water Works Association, Water Environment Federation, Washington, DC2005
- Effectiveness of different methods to control legionella in the water supply: ten-year experience in an Italian university hospital.J Hosp Infect. 2011; 77: 47-51
- Point-of-use membrane filtration and hyperchlorination to prevent patient exposure to rapidly growing mycobacteria in the potable water supply of a skilled nursing facility.Infect Control Hosp Epidemiol. 2011; 32: 837-844
- Reusable terminal tap water filters for nosocomial legionellosis prevention.Ann Hematol. 2005; 84: 403-405
- Point-of-use filtration method for the prevention of fungal contamination of hospital water.J Hosp Infect. 2010; 76: 56-59
- Point-of-use water filtration reduces endemic Pseudomonas aeruginosa infections on a surgical intensive care unit.Am J Infect Control. 2008; 36: 421-429
- Resolution of a Pseudomonas aeruginosa outbreak in a hematology unit with the use of disposable sterile water filters.Haematologica. 2006; 91: 983-985
- Hospital water point-of-use filtration: a complementary strategy to reduce the risk of nosocomial infection.Am J Infect Control. 2005; 33: S1-19
- Engineering waterborne Pseudomonas aeruginosa out of a critical care unit.Int J Hyg Environ Health. 2017; 220: 1014-1019
- Use of a disposable water filter for prevention of false-positive results due to nontuberculosis mycobacteria in a clinical laboratory performing routine acid-fast staining for tuberculosis.Appl Environ Microbiol. 2007; 73: 6296-6298
- Effectiveness of installing an antibacterial filter at water taps to prevent Legionella infections.J Hosp Infect. 2005; 61: 270-271
- Hygienic safety of reusable tap water filters (Germlyser) with an operating time of 4 or 8 weeks in a haematological oncology transplantation unit.BMC Infect Dis. 2007; 7: 45
- Experimental comparison of point-of-use filters for drinking water ultrafiltration.J Hosp Infect. 2017; 96: 172-176
- Tracking the spread routes of opportunistic premise plumbing pathogens in a haematology unit with water points-of-use protected by antimicrobial filters.J Hosp Infect. 2018; 98: 53-59
- Opportunistic premise plumbing pathogens: increasingly important pathogens in drinking water.Pathogens. 2015; 4: 373
- The hospital water supply as a source of nosocomial infections: a plea for action.Arch Intern Med. 2002; 162: 1483-1492
- Potable water as a cause of sporadic cases of community-acquired Legionnaires’ disease.N Engl J Med. 1992; 326: 151-155
- Effects of holding time and measurement error on culturing Legionella in environmental water samples.Water Res. 2014; 62: 293-301
- Testing for Legionella in healthcare facilities: evaluation of the reproducibility of Legionella test results and the impact of time on viability and variability.Am J Infect Control. 2013; 41: S69
- Ecology of Pseudomonas aeruginosa in the intensive care unit and the evolving role of water outlets as a reservoir of the organism.Am J Infect Control. 2005; 33: S41-S49
- Cluster of Pseudomonas infections among neonatal intensive care unit patients - Maryland.in: 2016 CDC EIS Conference, Atlanta, GAMay 2–5, 2017
- Investigation of healthcare-acquired infections associated with Pseudomonas aeruginosa biofilms in taps in neonatal units in Northern Ireland.J Hosp Infect. 2014; 86: 16-23
- Outbreak of Pseudomonas aeruginosa in a neonatal intensive care unit: are point-of-use filters useful?.Signa Vitae. 2017; 13: 75-79
- Infection control by point-of-use water filtration in an intensive care unit - a Hungarian case study.J Water Health. 2014; 12: 858-867
- Heterotrophic plate count bacteria—what is their significance in drinking water?.Int J Food Microbiol. 2004; 92: 265-274
- Lack of correlation between Legionella colonization and microbial population quantification using heterotrophic plate count and adenosine triphosphate bioluminescence measurement.Environ Monit Assess. 2015; 187: 393
- Water and surface microbiologic quality of point-of-use water filters: a comparative study.Am J Infect Control. 2016; 44: 1061-1062
- Management of risks from water and ice from ice machines for the very immunocompromised host: a process improvement project prompted by an outbreak of rapidly growing mycobacteria on a pediatric hematopoietic stem cell transplant (HSCT) unit.Infect Control Hosp Epidemiol. 2017; 38: 792-800
- Legionella pneumophila.in: Grota P APIC text of infection control and epidemiology. Association for Professionals in Infection Control and Epidemiology, Washington, DC2019
Solidarités M. Guide technique: l'eau dans les établissements de santé. Paris, France; 2005.
Conflicts of interest: None to report.